When a system uses both AC and DC power, two different ICs are required for Power Monitoring to ensure superior performance and accuracy. Many of the applications such as Solar Inverters, Smart Lighting and Cloud Servers often use both modes to maintain safe operation, AC as the main Power Supply while DC as backup Power Supply, or vice-versa. Microchip Technology Inc has solved this problem and eased up the process of power monitoring by launching a flexible dual-mode power monitoring IC that measures both AC and DC modes with an accuracy of 0.1 percent error. Power calculations and event monitoring are also one of the main features of this IC.
Source: Microchip Technology Inc.
Analog Device Inc. has introduced an energy-metering IC ADE9153A with auto-calibration for single phase energy measurement applications. This IC uses mSure technology to automatically calibrate the measurement system, reduced calibration time, and reduced equipment costs. This IC can be used with intelligent lighting, data centres, EV charging and industrial applications as it allows easy and accurate energy measurement.
Source: Analog Devices Inc.
Recently, Maxim Integrated Products Inc. have launched two new high performance and scalable Power Management Integrated Circuits (PMICs). With these ICs, mobile system designers can maximize performance per watt, while increasing system efficiency for computationally-intensive deep-learning systems-on-chip, FPGAs and application processors. These ICs, MAX77714 and MAX77752, find applications in augmented/virtual reality, gaming, solid-state drives (SSDs), security and Industrial Internet of Things (IIoTs) and many more handheld devices. Maxim Integrated Products Inc. claims that these ICs consume 40 percent less power than standard solutions, together with compact power factor and extended battery life.
Source: Maxim Integrated Products Inc.
When you study any of the upcoming new technologies, the main part of the system is Power Supply Unit. Power Supply Unit is the heart of the system, which supplies power to all the ICs, Controllers, Driving Circuits, etc. This places higher demands on the Power Supply Units. Recently, a company named Keysight Technologies have published an e-book titled “4 Ways to Build Your Power Supply Skill Set”. This e-book gives tips to be considered to design engineers while designing power supply.
Download link: E-book
Source: Keysight Technologies
Off-line PWM Controller from STMicroelectronics Boosts Efficiency, Flexibility, and Stability of 5-30V Power Supplies
STMicroelectronics’ STCH03 offline Pulse-Width Modulation (PWM) controller combines high integration with accurate constant-current output using primary-side regulation enabling economical mobile chargers, power adapters, or auxiliary supplies to meet stringent eco-design limits for average efficiency and standby power.
At heavier loads, the STCH03 maximizes efficiency by operating in quasi-resonant mode with zero-voltage switching (ZVS) controlled by detecting transformer demagnetization. The detection circuitry also provides for line-voltage feed-forward control, which ensures accurate constant-current regulation. Maintaining operation at the boundary of continuous (CCM) and discontinuous (DCM) transformer current, the STCH03 limits the converter’s maximum operating frequency to 167kHz depending on line/load conditions, and implements valley-skipping for best efficiency as the load reduces.
Energy-saving features including zero-power high-voltage startup circuitry, as well as low quiescent current and burst-mode switching when the load is very low or disconnected, keep standby power below 10mW to help chargers and adapters meet tough legislation such as the incoming CoC Tier 2 power supply efficiency specifications. Low peak current eliminates audible noise at light load or no load, and the STCH03 features an innovative adaptive under-voltage lockout (UVLO) to ensure consistent operation at low values of transformer auxiliary bias voltage.
With the advantage of accurate primary-side constant-current regulation, the STCH03 eliminates output-current sensing components, thereby reducing the charger bill of materials (BOM). The integrated startup circuitry, which consumes zero power when inactive, also saves external components.
The STCH03 contains many more features to help save external components and BOM cost, including over-temperature and over-voltage protection (OTP, OVP) with auto-restart or optional latching operation in the STCH03L variant. In addition, soft-start prevents high peak currents at startup, and output under-voltage protection lets the device operate safely in case of an output short-circuit or low output voltage under constant-current control.
- Advanced power management for ultra-low standby power consumption (under 10 mW at 230 VAC)
- Fully integrated primary side constant current output regulation (CC)
- 650 V embedded HV start-up circuit with zero power consumption.
- Quasi-resonant (QR) zero-voltage-switching (ZVS) operation
- Accurate and adjustable output OVP with options auto-restart (STCH03) or latched (STCH03L) after fault
- Output undervoltage protection (UVP) with auto-restart
- Input voltage feedforward compensation for mains-independent CC regulation
- Embedded thermal shutdown
- Intelligent frequency jitter for EMI suppression
The TPS3702 family of devices combines two comparators and a precision reference for overvoltage and undervoltage detection. The TPS3702 features a wide supply voltage range (2 V to 18 V) and highly accurate window threshold voltages (0.9% over temperature). The TPS3702 is designed for systems that require an active low signal if the voltage from the monitored power supply exits the accuracy band. The outputs can be pulled up to 18 V and can sink up to 10 mA. Unlike many other window comparators, the TPS3702 includes the resistors used to set the overvoltage and undervoltage thresholds internal to the device. These internal resistors allow for lower component counts and greatly simplifies the design because no additional margins are needed to account for the accuracy of external resistors.
The TPS3702 is designed to assert active low output signals when the monitored voltage is outside the window band.
Download PDF: Under Voltage and Over Voltage monitoring using TPS3702
Also there is one other IC from same manufacturer.
The TPS2400 has fixed turn-on and turn-off thresholds of 3 V and 6.9 V, respectively, making it an ideal overvoltage protector for 3.3 V and 5 V loads that are 6.9 V tolerant. However, many loads have an operating voltage that is greater than 6.9 V. To be compatible with these loads, the overvoltage threshold of the protector circuit can be
raised above 6.9 V.
Download PDF: Under Voltage and Over Voltage monitoring using TPS2400
Source: Texas Instrument
Till electronics came into the field of traction recently, the best suited drive for traction application was the dc series motor because of its inherent characteristics to give high torque at low speeds and vice-versa. The dc series motor was the best solution found for meeting the actual service as well as control requirements. On a fixed frequency, the asynchronous motor has a characteristic which is not well suited for traction application. However, this motor is of rugged construction when compared to a dc motor and requires much lower inputs for maintenance. Therefore its choice as a traction motor will always be preferred if control of the motor to suit the service requirements is possible. With the development of GTO thyristors, power electronics and micro processor control, controlling of any drive to suit specific requirements has become quite easy. In the circumstances, adoption of 3-phase induction motor for traction application has been tried for the past 10 years and has now become commercially viable proposition. The control is being achieved through variable voltage and variable frequency briefly referred to as WVF. Originally thyristors were used with commutation requirements for cut off. With the advent of GTO, the control has been made much simpler and more efficient thus use of 3-phase asynchronous motors for traction could also become financially viable.
A locomotive with 3-phase asynchronous motor drive has the following advantages :
- higher power capability due to high power/weight ratio,
- regeneration capability over a wide speed range,
- lesser maintenance,
- unity power factor at pantograph,
- higher adhesion.
Why 3-phase Drive is used?
The speed/torque characteristic of an induction motor supplied from a 3-phase voltage source of fixed frequency “f” is of the form shown in this figure.
It may be seen that at low speed, the torque is small and the stator current is high. The zone normally usable lies at the extreme from the point of maximum torque, in the vicinity of synchronous speed. For traction applications a high TE is necessary for starting and accelerating the train. Therefore, when constant torque is required, It is necessary to obtain whole series of characteristics curves such as shown in figure given below. This calls for change in synchronous speeds and therefore variable frequency.
The control of the ac induction motor drive in traction application is achieved in 3 stages
Constant torque mode:
The torque developed by a motor is proportional to the product of the magnetic flux in the air gap, and the rotor current. The applied voltage is proportional to the synchronous frequency and the magnetic flux in the air gap. To keep the magnetic flux constant, therefore, the applied voltage to the traction motor is to be made proportional to the synchronous speed.
The rotor current depends upon the slip frequency of the rotor. By keeping this constant, the rotor current is also kept constant. This is possible till the voltage is increased to the rated terminal voltage of the traction motor. Thus in this mode the control is achieved by increasing the voltage and frequency uniformly with respect to the actual speed of the rotation of the rotor and the required slip frequency.
Constant power mode:
In this mode the voltage is already reached to the rated voltage. By increasing the frequency, the magnetic flux in the air gap is reduced proportionately. By keeping the slip frequency constant, the motor current is kept constant. Thus the motor is made to give constant power output till the maximum service speed is reached.
Balancing speed stage:
Once the maximum pre-determined speed is achieved, the same power output from the traction motor may not be required and the output is to be matched to meet the resistance of the train for running at the balancing speed. This is achieved by suitably reducing the terminal voltage of the traction motor.
These functions are performed through micro processor control giving various inputs of parameters like voltage, current and speed.
In order to achieve the above control requirements, the converter/ inverters system with a dc link is adopted. The converter rectifies the ac voltage to dc and feeds it to the dc link. The dc link supplies power to the inverters. The converter output power is controlled by controlling the output current keeping the dc link voltage constant. The inverters output power is controlled by varying the terminal voltage initially till the full voltage is achieved. However the motor output current is kept constant.
The control of output current of the converter and output voltage of the inverters is achieved by pulse width modulation control.
The power circuit diagram of a typical 3-phase locomotive fitted with asynchronous motors is shown in figure given below.
Production of Rolling Stock
- Indian Railways have set up production units for Rolling stock and Rolling Stock components
- Apart from production for use of Indian Railways, these production units export Rolling Stock and components to many countries such as Burma, Bangladesh, Sri Lanka, Hungary, East Africa, Central Asian countries, East Asian countries etc.
- The following are the production units of Mechanical Department for production of different types of Rolling Stock:
List of Production Units
|Name of PU||Place where situated|
|Chittaranjan Locomotive Works||Chittaranjan|
|Diesel Locomotive Works||Varanasi|
|Integral Coach Factory||Chennai|
|Rail Coach Factory||Kapurthala|
|Rail Wheel Factory||Bangalore|
|Diesel Loco Modernisation Works||Patiala|
List of railway workshops under various railways
|Railway||Name of Workshop|
|North Western||20||Ajmer (Carriage)|
|25||Perambur (Carriage and Wagons)|
- Wagons are manufactured in various Railway workshops as well as some private firms.
Chittaranjan Loco Works, Chittaranjan, West Bengal
Diesel Loco Works, Varanasi
Diesel Modernization Works, Patiala
Parel Workshops, CR
Integral Coach Factory, Perambur
Rail Coach Factory, Kapurthala
Jessop & Co.
Burn & Co.
Braithwaite & Co.
Bharat Wagon & Engineering Co. (BEWL)
Titagarh Wagons Ltd.
Axles & Wheels
Wheel and Axle Plant (now Rail Wheel Factory)
Golden Rock Workshops
Motibagh Workshop, Nagpur
Coonoor Steam Shed
Rail Spring Karkhana
A fuse is a device that protects a circuit from an over current condition only.
It has a fusible link directly heated and destroyed by the current passing through it. A fuse contains a current-carrying element so that the heat generated by the flow of normal current through it doesnot cause it to melt the element; however, when an over current or short-circuit current flowsthrough the fuse, the fusible link will melt and open the circuit.
The Underwriter Laboratories (UL) classifies fuses by letters e.g. class CC, T, K, G, J, L, R, and so forth. The class letter may designate interrupting rating, physical dimensions, and degree of current limitation.
Construction of Fuse:
The typical fuse consists of an element which is surrounded by filler and enclosed by the fuse body. The element is welded or soldered to the fuse contacts (blades or ferrules).
The Element:The element provides the current path through the fuse. It generates heat at a rate dependent on its resistance and the load current.
The heat generated by the element is absorbed by the filler and passed through the fuse body to the surrounding air. The filler material, such as quartz sand, provides effective heat transfer and allows for the small element cross-section typical in modern fuses. The effective heat transfer allows the fuse to carry harmless overloads. The small element cross section melts quickly under short-circuit conditions. The filler also aids fuse performance by absorbing arc energy when the fuse clears an overload or short circuit.
Inverse Time Characteristic of Fuse:
When a sustained overload occurs, the element will generate heat at a faster rate than the heat can be passed to the filler. If the overload persists, the element will reach its melting point and open. Increasing the applied current will heat the element faster and cause the fuse to open sooner. Thus, fuses have an inverse time current characteristic: that is the greater the over current, the less time required for the fuse to open the circuit.
This characteristic is desirable because it parallels the characteristics of conductors, motors, transformers, and other electrical apparatus. These components can carry low-level overloads for relatively long periods without damage. However, under high-current conditions, damage can occur quickly. Because of its inverse time current characteristic, a properly applied fuse can provide effective protection over a broad current range, from low-level overloads to high-level short circuits.
Types of Fuse:
A fuse unit essentially consists of a metal fuse element or link, a set of contacts between which it is fixed and a body to support and isolate them. Many types of fuses also have some means for extinguishing the arc which appears when the fuse element melts. In general, there are two categories of fuses.
(1) Low voltage fuses.
(2) High voltage fuses.
Usually isolating switches are provided in series with fuses where it is necessary to permit fuses to be replaced or rewired with safety.
In absence of such isolation means, the fuses must be so shielded as to protect the user against accidental contact with the live metal when the fuse is being inserted or removed.
(1) Low Voltage Fuse:
Low voltage fuses can be further divided into two classes namely
a) Semi enclosed (Rewireable Type Fuse / Kit Kat Fuse):
The most commonly used fuse in ‘house wiring’ and small current circuit is the semi-enclosed or rewire able fuse. (Sometime known as KIT-KAT type fuse). It consist of a porcelain base carrying the fixed contacts to which the incoming and outgoing live or phase wires are connected and a porcelain fuse carrier holding the fuse element, consisting of one or more strands of fuse wire, stretched between its terminals.
The fuse carrier is a separate part and can be taken out or inserted in the base without risk, even without opening the main switch. If fuse holder or carrier gets damaged during use, it may be replaced without replacing the complete unit.
The actual fusing current will be about twice the rated current. When two or more fuse wire are used, the wires should be kept apart and a derating factor of 0.7 to 0.8 should be employed to arrive at the total fuse rating.
The specification for re wire able fuses are covered by IS: 2086-1963. Standard ratings are 6, 16, 32, 63, and 100A.
A fuse wire of any rating does not exceeding the rating of the fuse. We use 80 A fuse wire in a 100 A fuse, but not in the 63 A fuse. On occurrence of a fault, the fuse element blows off and the circuit is interrupted. The fuse carrier is pulled out, the blown out fuse element is replaced by new one and the supply can is resorted by re-inserting the fuse carrier in the base.
Easily removal or replacement without any danger of coming into the contact with a lie part.
Negligible replacement cost
Lack of Discrimination.
Small time lag.
Low rupturing capacity.
No current limiting feature.
Slow speed of operations.
b) Totally Enclosed(Cartridge Type Fuse)
The fuse element is enclosed in a totally enclosed container and is provided with metal contacts on both sides. These fuses are further classified as
I) D- Type Cartridges Fuses
It is a non interchangeable fuse comprising fuse base, adapter ring, cartridge and a fuse cap. The cartridge is pushed in the fuse cap and the cap is screwed on the fuse base. On complete screwing the cartridge tip touches the conductor and circuit between the two terminals is completed through the fuse link. The standard ratings are 6, 16, 32, and 63 amperes.
Breaking or rupturing capacity: 4k A for 2 and 4 ampere fuses the 16k A for 63 A fuses.
Ratings of D Type Cartridge fuses: 2, 4, 6, 10, 16, 25, 30, 50, 63
D-type cartridge fuse have none of the drawbacks of the re wire able fuses. Their operation is reliable. Coordination and discrimination to a reasonable extent and achieved with them.
II) Link type Cartridge or High Rupturing Capacity (HRC)
Where large numbers of concentrations of powers are concerned, as in the modern distribution system, it is essential that fuses should have a definite known breaking capacity and also this breaking capacity should have a high value.
High rupturing capacity cartridge fuse, commonly called HRC cartridge fuses, have been designed and developed after intensive research by manufactures and supply engineers in his direction.
The usual fusing factor for the link fuses is 1.45. The fuses for special applications may have as low as a fusing factor as 1.2.
Knife Blade Type HRC Fuse:
It can be replaced on a live circuit at no load with the help of a special insulated fuse puller.
Bolted Type HRC Link Fuse:
It has two conducting plates on either ends. These are bolted on the plates of the fuse base. Such a fuse needs an additional switch so that the fuse can be taken out without getting a shock.
Ratings of HRC fuses: 2, 4, 6, 10, 16, 25, 30, 50, 63, 80, 100, 125, 160, 200, 250, 320, 400, 500, 630,800, 1000 and 1,250 amperes.
An electrical relay is a switch that is used for controlling circuits. Today you’ll learn about different types of electrical relays.
Electromagnetic attraction type
The magnetic force produced by undesired current attracts the armature of the relay. Electromagnetic attraction type relays can operate on either a.c or d.c quantities. They are further divided into three types:
- Attracted armature type
- Solenoid type
- Balance beam type
Induction type relay
The working of Induction type relays relies on the electromagnetic induction phenomenon. They are only used for a.c quantities. They are further classified into two groups:
- Induction cup relay
- Induction disc relay
Directional type relay
Directional type relays operate on the direction of current and power. They are classified into two groups:
- Reverse current
- Reverse power
The tripping instant in time-based relays can be controlled. Such relays are classified into three classes:
- Instantaneous type relays
- Definite time lag type
- Inverse time lag type
- Capacitor type
- Electronic type
Distance type relay
Distance type relays contain two coils. One of which is energized using current and another one with voltage. The voltage to current ratio is measured and working of distance relays is based on this voltage to current ratio. They are further classified into three distinctive groups:
A differential relay compares the difference of quantity entering and leaving the system. They are also classified into two groups:
- Differential current
- Differential voltage
The relay operates when the temperature rises above certain limit due to current.
The sensed quantities are first rectified and then provided to relay coil.
It is a permanent magnet d.c relay in which he coil is free to rotate.
Gas actuated relay
In such relays, the gas pressure is adjusted in a manner so as to trip the relay coils.
Numerical/Microprocessor based relay
Microprocessor based relays are the most advanced type of programmable relays.
Reed switch relays
These are simple and compact relays. The basic reed relay is simple reed switch which has a winding wrapped around the relay. They are manufactured in many DIP and SIP packages as well as winding free reeds are also available.
Static relays – Solid State Relays
Static relays are composed of electronic components. Such relays are composed of transistors, diodes, integrated circuits, resistors and other electronic components. An essential part of such relays is a comparator which takes two or more current/voltages as input and provides an output.
Frequency Monitoring relays
The frequency of voltage plays key role in electrical power networks. The working of various electrical machines, generators, and mechanisms heavily relies on frequency. Frequency relays continuously monitor the operating frequency of system and trip on the variations.
As the name indicates, the working of thermal relays depends on the temperature of the equipment. They can either directly detect the temperature or can detect the current overloading conditions.
Motor load monitoring relays
Such relays monitor the load condition and operate under specified conditions. These relays can be based on current measurement or on cosφ based.
Insulation monitoring relays
Insulation monitoring relays continuously monitor the insulator. Whenever insulation fault occurs it immediately trips when the voltage drops behind specified threshold value.
Liquid monitoring relays
They are used to monitor regulator and control of liquid fluids.
One part of such relays in electro-mechanical while another part is solid state electronics.
General purpose relays
These are different types of relays whose working principle is based on either of above types.